There are many paths to the PE exam, and it is important that you prepare for this exam with your own obligations and experiences in mind. See Casey’s tips for passing the exam!
Open or Closed? Does My Parking Garage Require Exhaust?
“Is the parking garage open or closed?”
This is, and should be, one of the first questions asked by MEP engineers when a project containing a parking garage is kicked off. Enclosed parking garages require significant design efforts from a mechanical and architectural perspective.
What The Code Says
The 2015 International Building Code outlines what defines an “open” parking garage in Section 406.5.2:
- Exterior side of the structure shall have uniformly distributed openings on two or more sides
- Area of these openings shall be at least 20% of the total perimeter wall area of each tier
- Aggregate length of the openings shall be at least 40% of the perimeter of the tier (Exception: Not required if openings are uniformly distributed over two opposing sides of the building)
If these requirements are met, the garage is considered open is assumed to be naturally ventilated. If they are not, the garage is required to be mechanically ventilated.
The requirements for ventilating an enclosed parking garage can vary depending on the jurisdiction. In Austin, they are outlined in the 2015 Uniform Mechanical Code. Table 403.7 indicates that the minimum exhaust rate for an enclosed parking garage is 0.75 cfm per square foot.
How To Make It Happen
This is usually accomplished with an exhaust fan on each floor of the garage. These systems are required to operate continuously unless they are designed to operate automatically upon detection of vehicle operation or the presence of occupants. This is usually accomplished by providing carbon monoxide detectors throughout the parking garage and interlocking the exhaust fan operation with the carbon monoxide detection system on each level of the parking garage. When carbon monoxide levels in the garage reach a specified level, the associated exhaust fan will be enabled.
The UMC also requires that parking garage exhaust be discharged at the building exterior. It must be 10 feet above grade, 10 feet from any openings into the building (including operable windows), and 10 feet from the property line.
Early Coordination Is Key
A chase must often be provided (especially in the case of underground parking garages) to allow the exhaust to discharge 10 feet above grade. Not only must the chase be sized for the exhaust airflow, but it also must be able to accommodate the louvers at the discharge point, which can often be very large. It is critical, therefore, that coordination happen early in the design process as this can have a significant impact on the overall building design. Enclosed parking garages require a significant design effort but headaches can be avoided with some early coordination.
Share this post
Share this post
Of all the contingencies facility owners and managers planned for in 2020, a global pandemic was probably pretty low on the list. WGI has some key strategies that facility owners and managers leverage to keep your operations functioning effectively and safely amid this global pandemic.
WGI is celebrating the engineering profession with our PE’s and aspiring PE’s around the nation for the fourth annual Professional Engineers Day!
Here’s what to know and some tips for moving into the new normal of parking garage management during the coronavirus pandemic.
Strategies for a Healthier Parking Facility. Promote public health and protect patrons with these operational management strategies.
Investing in VRF technology on your next project can reduce energy costs, improve occupant comfort, reduce mechanical unit noise and reduce down time. WGI’s MEP Engineering experts can help you design and select the right system.